Recessed DOUBLE TOILET TISSUE HOLDER WITH HOOD
Includes hood. Recessed Double Toilet Tissue Holder holds and dispenses all standard core roll tissue up to 6’’ diameter (Ø152) roll (holds two (2) rolls). Fabricated of stainless steel type 304 alloy 18-8. Roller is chrome plated high impact resistant ABS plastic and spring-loaded.
Select product with options from Model Options drop-down, below:
- If drywall installation is required, add suffix “D” to model number. If wetwall installation is required, add “W” to model number (no clamp is required for wetwall).
- Optional finish and mounting style must be specified as either bright or satin and wet or drywall. Specify finish and mounting by adding code suffixes to model number (i.e. 74022-HSD or 74022-HSW or 74022-HBD or 74022-HBW).
- -B: Bright Finish
- -S: Satin Finish
- -H: With Hood
- -D: Drywall Holes
- -W: Wetwall Lugs
- For theft-resistant spindle, add R-009 after model number.
For Wet wall Recessed Mounting: Slop grout into rough wall opening. Apply grout to back of unit and on perforated lugs and push unit into opening to seat flange flush with wall face. Allow unit to set and grout to cure before use.
For Standard Dry Wall Recessed Mounting: Use four (4) No 10 stainless steel Philips flat or oval head self tapping or wood screws (by others) of suitable length to penetrate blocking in back of RWO by approximately 1/2″ (13). Apply a continuous bead of silicone sealant (by others) behind flange. Tighten screws to hold flange tight against finished wall face. Wipe off excess sealant immediately.
Optional Method for Dry Wall Recessed Mounting: Order two (2) separate items Model No 39 dry wall clamps. Loosely attach clamps to the back of the unit with four (4) stainless steel Philips flat or oval head No 10B (or 10AB or 10BP) self tapping screws (provided by others to suit wall conditions) through dimpled holes at back of shell. Apply a continuous bead of silicone sealant (by others) behind flange. Insert into RWO and adjust clamps so that they grip inside wall surface through opening. Secure accessory to clamps and wall by tightening screws. Wipe off excess sealant immediately.
For compliance with ADA Accessibility Guidelines install unit with centerline of rollers 19″ (483) min AFF to 42″ (1067) max AFF and 7″ (178) min to 9″ (229) max from front of commode to centerline of dispenser. Rough wall opening
(RWO) required is 11-3/4″ W x 5-1/2″ H x 2″ D (298 x 140 x 51 mm)
12 5⁄8″ x 6 5⁄16″ (320 x 160 mm)
11-3/4″ W x 5-1/2″ H x 2″ D (298 x 140 x 51 mm)